Siemens: Telecontrol for Simatic controllers
Communication processor for telecontrol applications using Simatic S7-1200 controllers
Transferring measured values from outdoor areas to central control center
Automatic e-mails for maintenance staff
The Siemens Industry Automation Division has developed a new communication processor for telecontrol applications based on Simatic S7-1200 controllers. Simatic CP 1243-1 DNP3 from the TeleControl Professional product range connects the controller to a control center, such as a process control system, via DNP3 (Distributed Network Protocol). A typical use case for this is the transfer of measured values in widely spread outdoor areas to a central station, for example in sewage and water treatment plants, district heating networks and pump stations, as well as in oil and gas supply, energy distribution and transportation systems.
Simatic CP 1243-1 DNP3 transfers measured values, setpoint values and alarms to the control station cyclically or event-based. In the STEP 7 engineering tool, the user simply selects the data to be transferred from the Simatic S7-1200 CPU and specifies the required communication parameters. Communication with the control center is based on the established telecontrol protocol according to DNP3 specification 2 (2007/2009) including security mechanisms for secure data transfer via wide area networks. In addition to data transfer, the communication processor also has an e-mail function, for example to inform maintenance staff automatically about previously defined events, such as threshold values being
Simatic CP 1243-1 DNP3 can buffer up to 64,000 values with time stamp in order to prevent data loss when a connection fails. When the connection is re-established, the buffered values are automatically transferred to the control center in the right chronological order. Comprehensive diagnostic options, locally via LEDs or in the STEP 7 engineering tool, offer the user fast and clear analysis of the station status. The communication processor is connected to the local communication network in the outdoor area via Ethernet interface. Appropriate transmission components, such as the Scalance M874 industrial router, are available for remote communication from the local network to the control station.
Source: Gerhard Stauss, Siemens AG
Sept. 10, 2013
Worldwide more than 100,000
from the editors of
Oil & Gas Journal
and Offshore Magazine:
here ... and see what we have designed, produced, published and promoted for WIKA
and FMC Technologies ... and what we would like to do for you.
.PennWell Petroleum Group:
OGJ - Oil & Gas Journal
Oil & Gas Financial Journal
Oil, Gas & Petrochem
+ + +
For more information, media
sample copies please contact